Secondary power distribution up to 600V in areas with soft soils where rodents are not present.
Used for secondary distribution and underground service at 600 volts or less, either direct burial or in ducts, in areas with soft soils where rodents are not present.
Secondary power distribution up to 600V in areas with soft soils where rodents are not present
Conductors are stranded, compressed 1350-H16/H26 aluminum insulated with vulcanized interlinked polyethylene. Neutrals are triple yellow extruded stripe. Neutrals have sequential footage markers. Conductors are durably surface printed for identification. Three phase conductors and one neutral conductor are cabled together to produce the quadruplex cabled together to produce the quadruplex cable configuration.
Paige’s quadruplex or paralleled 600 volt secondary UD cable meets or exceeds the following applicable ASTM specifications.
Paige’s quadruplex 600 volt secondary UD cable meets or exceeds all applicable requirements of ICEA S-105-692 for cross-linked polyethylene insulated conductors and UL Standard 854 for Type USE-2.
|CODE WORD||PHASE CONDUCTOR||NEUTRAL||DIAMETER (mils)||WEIGHT PER 1000 FOOT (lbs.)||ALLOWABLE AMPACITANCE|
|Size (AWG)||Stranding||Insulation Thick (mils)||Size (AWG)||Stranding||Insulation Thick (mils)||Single Pase Conductor||Complete Cable||Direct Burial||In Ducts|
|QUADRUPLEX WITH YELLOW EXTRUDED STRIPE NEUTRAL|
|±Ampacity 90°C conductor temperature 20°C ambient, RHO 90, 100% load factor for three conductor triplex with neutral carrying only unbalanced load.|